- Exhibit code：SN009709
- Size of exhibits（mm）：25-630 mm2
- Model of exhibits：
- Materials of exhibits：
- Color of exhibits：Black,Orange,Red and so on
- Place of delivery：China-SHAN DONG -DE ZHOU
- Raw material production place：China-SHAN DONG -DE ZHOU
- Features of exhibits：
Details of exhibits
1. Stranded compacted copper conductor class 2
2. Extruded semi-conductive conductor screen
3. XLPE insulation
4. Extruded semi-conductive insulation screen
5. Copper tape screen
6. PP Filling
7. Non-woven fabrics wrapping
8. PVC inner sheath
9. Steel wire armored
10. Non-woven fabrics wrapping
11. LSZH(Low Smoke Zero Halogen) outer sheath
YJV32-Copper Conductor XLPE Insulated Steel Wire Armoured LSZH Sheathed Power&Mains Cable.
Copper XLPE SWA Armoured Cable is suitable for using in power distribution networks or fixed installations for industrial equipments with rated voltage up to and including 1.8/3kV, 3.6/6kV, 6/10kV 8.7/15kV, 12/20kV, 21/35kV, 26/35kV.
GB/T12706-2008,IEC,BS,VDE,ASTM and etc. upon request.
Rated Voltage (Uo/U)
1.8/3kV, 3.6/6kV, 6/10kV 8.7/15kV, 12/20kV, 21/35kV, 26/35kV.
Copper Conductor/XLPE Insulation/Steel Wire Armoured/LSZH Sheath
Number of conductors:1,3
The conductors shall comply with the requirement given in IEC
XLPE(Cross-linked Polyethylene) according to IEC
PVC(Polyaluminium Chloride) according to IEC
Copper Tape Screen
Maximum conductor temperature in normal use: 90℃
Maximum shall not exceed 250℃(5s Max,Duration)
Ambient temperature under installation shall not be below 0℃
Minimum bending radius
The bending radius of cable: (D-Diameter of cable)
For Three Core Cable————————————-≥15D
For Single Core Cable————————————-≥20D
The three core cables are designed for distribution of electrical power with nominal voltage Uo/U ranging from 3.6/6.6KV to 19/33KV and frequency 50Hz.
They are suitable for installation mostly in power supply stations, indoors and in cable ducts, outdoors, underground and in water as well as for installation on cable trays for industries, switchboards and power stations.
BS 7835 (LSZH Version)
Plain annealed copper or aluminium complying with IEC 60228/BS 6360. Copper conductors shall be stranded (class 2) and aluminium conductors shall be either solid or stranded (class 2).
Extruded layer of semi-conducting cross-linkable compound is applied over the conductor and shall cover the surface completely. The minimum thickness is 0.3mm and the maximum resistivity shall not exceed 500 Ohm-m at 90°C.
Insulation is of cross-linked polyethylene compound XLPE (GP8) conforming to BS 7655-1.3 or EPR (GP7), conforming to BS 7655-1.2.
Table 1. Insulation Thickness
Nom. Cross Section Area
Insulation Thickness at Nominal Voltage
70 – 185
Extruded layer of semi-conducting cross-linkable compound is applied over the insulation. The extruded semi-conducting layer shall consist of bonded or cold strippable semi-conducting compound capable of removal for jointing or terminating. As an option, a semi-conducting tape may be applied over the extruded semi-conducting layer as a bedding for the metallic layer. The minimum thickness is 0.3 mm and the maximum resistivity is 500 Ohm-m at 90°C. The screen is tightly fitted to the insulation to exclude all air voids and can be easily hand stripped on site.
Inner Covering & Fillers
For cables with a collective metallic layer or cables with a metallic layer over each individual cores with additional collective metallic layers, semi-conducting inner covering and fillers shall be applied over the laid up cores. The inner covering is made of non hygroscopic material, except if the cable is to be made longitudinally watertight. The inner covering shall be extruded or lapped.
The approximate thickness of extruded inner coverings is given in Table 2:
Table 2. Approximate Thickness of Extruded Inner Coverings
Ficititous Diameter over Laid Up Cores
Approx. Thickress of Extruded Inner Covering
*The approximate thickness of lapped inner coverings shall be 0.6mm.
The metallic layer shall be applied over each core or applied as a collective screen. The metallic screen shall consist of either copper tapes or a concentric layer of copper wires or a combination of tapes and wires. The metallic layer provides an earth fault current path, capable of withstanding fault current to earth of 1000A for one second at maximum temperature 160°C. Copper wires are applied over the conducting water blocking layer with a minimum diameter of 0.5mm. And over the copper wires, copper tape with minimum thickness of 0.1mm can be applied helically with overlap.
Total cross section of copper wire screen is shown in table 3:
Nominal Cross-Section Area of Cable
Minimum Cross-Section of Copper Wire Screen Area
DC Resistance of the Copper Wire Screen
up to 120
Table 3. Minimum Total Cross Section of Copper Wire Screen & DC Resistance of The Screen
Separation Sheath (for armoured cable)
The separation sheath comprises a layer of extruded PVC, PE or LSZH. The nominal thickness is calculated by 0.02Du + 0.6mm where Du is the fictitious diameter under the sheath in mm. The nominal separation sheath thickness shall not be less than 1.2mm.
Armour (for armoured cable)
The armour consists of galvanized steel wire applied over the inner covering with diameter specified as in Table 4.
Table 4. Armour Wire Diameter
Fictitiious Diameter under the Armour
Armour Wire Diameter
Overall sheath comprises a layer of extruded either PVC type 9 conforming to BS 7665-4.2 or MDPE type TS2 conforming to BS 7655-10.1; LSZH can be offered as an option. The over sheath is normally black in colour. When a DC voltage test is to be performed on the over sheath, a semi-conducting layer such as graphite coating shall be applied over the surface of the extruded over sheath. The nominal over sheath thickness is calculated by 0.035+D where D is the diameter immediately under the over sheath in mm. For cables with the over sheath not applied over the armour, the nominal over sheath thickness shall not be less than 1.4mm. And for cables with over sheath applied over the armour, the nominal over sheath thickness shall not be less than 1.8mm.
up to 90°C
-5°C ( PVC or LSZH sheath ); -20°C ( PE sheath )
Short Circuit Temperature
250°C (short circuit duration up to 5 seconds)
15 x OD
Table 5. Nominal /Operating /Test Voltages
Rated Voltage Uo/U
Operating Voltage (Um)
Testing Voltage (rms)
Waiting to accept invitation...
Invite you to a video call
Please login to proceed.